If this is your first visit, be sure to
check out the FAQ by clicking the
link above. You will be required to register
before you can post: click the register link above to proceed. To start viewing messages,
select the forum that you want to visit from the selection below.
u need to open the fixture ,look inside to see if it has a multi tap ballast (120v,208v,240v,277v) or just 480v. if it is a multi tap, and you want too wire this with 120v,you use the 120v lead (wire this lead to the black wire) and the common lead(wire the white or neutral conductor to this lead). cap all the other leads off individually with a wire nut. if it is just 480v,it will not work at a residence.
is this what it looks like? http://www.hubbelloutdoor.com/produc...iniliter_v.pdf