If this is your first visit, be sure to
check out the FAQ by clicking the
link above. You will be required to register
before you can post: click the register link above to proceed. To start viewing messages,
select the forum that you want to visit from the selection below.
I recently had the exact same problem. I ran a 3/4" gas line about 60' underground to a 350btu pool heater.I read out interesting and informative ideas.This will be helpful for me.Thanks everyone...
Then be aware that the line you installed, unless it's high pressure, is woefully undersized for your application. A basic sizing chart shows you will only get approximately 138,000 btu across that distance using low pressure gas.