Well went on a call yesterday. Restaurant , the only thing that was backing up was the bathrooms in the back. Toilet was pulled when I got there..sweet...I just could not get a cable through..Tried 7/8", 5/8" nothing was working..Tried using a trap leader. I was thinking they used a double t-wye . Not happening .Up on the roof I went with the k-60 I hand fed all 150' of cable ..Nothing..Apparently the 3" stack vent was not connecting to that branch..Now I'm getting pissed..Pack everything up go back down stairs and keep trying..A buddy came by to give me a hand..Say's "Why dont you try going down the lavy drain" I really wanted to get my 7/8" cables down that line but had to settle for the 5/8"..While I was snaking I had my buddy use the closet supply to fill the line ..Then he says "There it goes"..I was so happy just to get it.Had I just went down the lavy drain after several attempts I would have been out of there a lot sooner. Bottom line ,stoppage was cleared but looking for a cable / head combo for back to back toilets.I would have love to have had a camera to see why nothing was working
No announcement yet.
Back to back toilets !