If this is your first visit, be sure to
check out the FAQ by clicking the
link above. You will be required to register
before you can post: click the register link above to proceed. To start viewing messages,
select the forum that you want to visit from the selection below.
I have the same toner unit and used it for years when in the Telco industry. I have since used it in the method that Newman is suggesting and worked great. I actually just did the same thing about 2 months ago with some 12/2 wire in the basement and it worked great. I wonder if perhaps the batteries are low in either the unit or wand side? You did verify the wires are not shorted? Even with the volume turned to high when using mine with telephone wire I could get the signal radiating from the Dmarc from a couple feet away. With larger diameter electrical copper wire the signal distance is even further in my experience.
The tracer did pick up the signal for about 20 feet, but it disappeared after, and I was under the delusion that this wire was going all the way to the breaker panel. I made the assumption that it was somehow buried deeper in the wall and the tracer did not get enough signal strength.
I borrowed a 3M instrument that tells you how long the wire connected to it is, and I was told 27', which would be 60' short from the breaker box.
As it turned out, I opened the wall at the point where the signal stopped and found a junction box that was meant to be an electrical outlet, but the drywallers just covered it and did not cut out the opening. As soon as I connected the wires inside this box, everything got to work properly.
No intention to hide it. It is being fixed properly, and when it's done, one will not be able to tell that there was a hole in the wall before. I am a great believer in the "If it's worth doing, it's worth doing right".
Glad the TDR did the job. I read this thread the other day and couldn't come up with anything different to try than others had suggested. It didn't even down on me to think about a TDR to measure the cable length.
Like PapaDan says: "My mind is not what it used to be...and another thing; My mind..."
"When we build let us think we build forever. Let it not be for present delight nor for present use alone. Let it be such work that our descendants will thank us for, and let us think, as we lay stone upon stone, that a time is to come when these stones will be held sacred because our hands have touched them, and that men will say, as they look upon the labor and wrought substance of them, "See! This our fathers did for us."
John Ruskin (1819 - 1900)
Why did not the inspector or the electrician find the problem before?
Push sticks/blocks Save Fingers
"The true measure of a man is how he treats someone who can do him absolutely no good."
attributed to Samuel Johnson
PUBLIC NOTICE: Due to recent budget cuts, the rising cost of electricity, gas, and oil...plus the current state of the economy............the light at the end of the tunnel, has been turned off.
A friend, who is an installer for Bell Canada brought this handheld instrument over, I am not sure what the model or name is, but I saw a 3M logo on it. He hooked it to the wire and it showed on the display how long it was.