If this is your first visit, be sure to
check out the FAQ by clicking the
link above. You will be required to register
before you can post: click the register link above to proceed. To start viewing messages,
select the forum that you want to visit from the selection below.
for commercal kitchen repcaitles [ outlets ] it will depending on what appalince it will be on IMO it will be wise idea to run indepent if you are expecting very high power stuff there and also make sure you have it on gfci repectale or breaker depending on the area.
you can label the repectale cover for which breaker it goes but not all place done that so it willbe nice if it was labeled there.
my past experince with commercal kitchen repectailes circuits normally i run 20 amp circuits with 20 amp repectailes devices either gfci repectale or plain face type depending on where it runs [ you may have to check with your local codes they may have more addments to the codes so check it out ]