I have inherited an unfinished garage sub panel installation. It is ran to an attached garage 50' from the main house panel. A 100 amp double pole feeds triple 2 Al to a QO sub. The neutral is not bonded at the sub. One wire with a red stripe is on what looks like the hot. The other wire is on the opposite lug. The bare is on what looks like the neutral lug. There is a ground bus screwed in the panel as well with nothing on it. The feeder wire is only three wires. What should be the next step, starting over or finishing a pretty good idea. The house has 200 amp service in a Cutler panel. Both insulated wires are on the feed breaker and the bare is on the ground bus in the main panel. Any info is appreciated.
No announcement yet.