I have inherited an unfinished garage sub panel installation. It is ran to an attached garage 50' from the main house panel. A 100 amp double pole feeds triple 2 Al to a QO sub. The neutral is not bonded at the sub. One wire with a red stripe is on what looks like the hot. The other wire is on the opposite lug. The bare is on what looks like the neutral lug. There is a ground bus screwed in the panel as well with nothing on it. The feeder wire is only three wires. What should be the next step, starting over or finishing a pretty good idea. The house has 200 amp service in a Cutler panel. Both insulated wires are on the feed breaker and the bare is on the ground bus in the main panel. Any info is appreciated.
How To Post Images
Want to know the how to upload images to your posts? Image Posting Tutorial
panel wiringPage Title Module
Move Remove Collapse