If this is your first visit, be sure to
check out the FAQ by clicking the
link above. You will be required to register
before you can post: click the register link above to proceed. To start viewing messages,
select the forum that you want to visit from the selection below.
You'd have to purge the line to avoid contamination
which in those small lines would be hell to get out.
Last mini-split I put in (Sanyo 12KHS71) the manual
said to put a little (R410A compatible) refrigerant oil
on the flare connections.
I noticed they didn't do that on the show.
Light is faster than sound. That's why some people seem really bright until you hear them speak.
--------------- “If I had my life to live over again, I'd be a plumber.” - Albert Einstein
--------- "Its a table saw.... Do you know where your fingers are?"
--------- sigpic http://www.helmetstohardhats.com/
We have installed 30+ Fujitsu mini splits, pipe cut square, reamed with tuning end facing the ground so pieces can't get into system. Properly flared so flare only covers about 3/4 of the flare face of the fitting. Wiped with some ester based oil and properly tightened. I have a set of torque wrenches CPS brand that I ordered at a Fujitsu school. About a C-note if I remember right.
1/4" 150 in lbs
3/8" 300 in lbs
1/2" 500 in lbs
5/8" 650 in lbs
Test the system side with nitrogen @500 psi. Not one leak on any one of these systems. Vac the system down to 1000 micron and your golden.
Proper installation of any thing is the key to no problems.
WE LIVE IN THE LAND OF THE FREE,
ONLY BECAUSE OF THE BRAVE
this is kinda off topic
but flare fittings are used on 3000 psi hydraulics, called JIC fittings, there 37 degree.
so the fitting is not necessary a low psi fitting,
I think the question may be is there better connections, and I do think there is.
Push sticks/blocks Save Fingers
"The true measure of a man is how he treats someone who can do him absolutely no good."
attributed to Samuel Johnson
PUBLIC NOTICE: Due to recent budget cuts, the rising cost of electricity, gas, and oil...plus the current state of the economy............the light at the end of the tunnel, has been turned off.
Thanks James. I don't want to beat it to death but want to make sure I get it.
The same lines doing the same thing on other systems can be connected with flared fittings?
Example: 2 Ton Trane Residential HVAC unit that sits outside on a pad.
The short answer is Yes.
For me a brazed connection is more desirable, but there are situations where a mechanical fitting is more suited. If you ever worked on larger tonnage compressors you would learn to appreciate mechanical connections like the Rotolock.
I've ran across many split systems that the connections were soft soldered together. Usually by plumbers who do hvac also or the local yokel handymen types who can only drop a bird turd with silfos.