Had a call for lack of volume on the hot water. Checked all the usual culprits and finally cut the line coming out of the tank and found this small marble stuck in the first elbow!! Don't remember who made that particular tank ( might have been a state ) but the marble was from the cold inlet and was supposed to work as a backflow-antisyphon device. Needless to say, yes the dip tube also needed replacing.
Login or Sign Up
- Log in with Facebook