Installed heater on single bath commercial building works great with .5 gpm aerator supplied when hot water only is on but when cold water is turned on to mix or cool down water heater turns off. Called manufacturer and they suggested .75 gpm aerator to fix. Did not work it is hooked up exactly like their brochure suggested any ideas to make this work without replacing or should i replace and return. HELP
No announcement yet.
EEMAX point of use water heater help