Are figure five fittings allowed in your code area or do you even use them in a complete horizontal position? This is a more frequent practice here nowadays to put these in and one branch will be a toilet and the other side is a fixture that does not get much use. So whats happening is paper is clogging in the outfall of fitting. Then when you cable the drain the paper is so packed in there it makes your cable jump to the other side...and of course you can't go through the top because its capped and not accessible. This is so frustrating when the line is over heard 14 to 16 feet in the air or under concrete. So any input on this practice?
No announcement yet.
Figure Five Fitting