If this is your first visit, be sure to
check out the FAQ by clicking the
link above. You will be required to register
before you can post: click the register link above to proceed. To start viewing messages,
select the forum that you want to visit from the selection below.
Its on a Aerco Benchmark so seeing the flame is out. I walked by it and heard the thing hunting. They had electrical issues so they decided to change the gas spring...go figure. The gas valve wasn't hardly opening up 20% at high fire and would go off when it was at low fire. They over size the gas valve. They use 2" and can get by with 3/4".