So installed this uv filter on Saturday it's a uv Trojan max I've installed a few of them however this one didn't come with any of the options I am used to no flow sensor no solenoid that dumps the heated water it seemed almost to plain as if I was missing something the customer is a electrical engineer really don't want him to have any issues later the two blue filter are a double median cartridge the pure filter that's not in the picture is a spin down 130 micron then the first chamber is 50micron step down with 25 micron second median. The nect cartridge is a 15 to 1 micron the uv recommend no courser then 5 micron so figured this should be atiquette. I put a bypass on the uv we filled both chambers with a 30% bleach solution and flushed thru the bypass and ran water at every fixture till the smell of bleach was gone. Any positive criticism is more then welcomed I don't do a lot of water treatment unfortunately the guy that does is two hours away each way and has horrible customer service so I get roped in to install and maintaining them every once in a while. Hope I didn't do anything to stupid. Thanks seanny
No announcement yet.
Uv filter this look right?