Re: Replaced piping - still low pressure
it sounds like you have dirt/ debris in a strainer/ regulator.
Originally Posted by JRO
does your pipe enter the house above grade outside?
is there a pressure regulator installed there?
if so, remove the strainer cap and flush out.
a pressure gage is similar to a doctors blood pressure test.
what's your static pressure/ nothing running?
what's your drop off pressure when you open a faucet?
pressure drops a lot, it's a volume thing.
pressure low without anything running, it can be a bad regulator.
how's the neighbors flow?
yes, water meters can go bad and can restrict the flow. i've had it on more than 1 occasion.
Tags for this Thread