I'm installing a sub panel in my basement, my main panel is in my garage, I have surface mount 1.250 PVC conduit and installed my 40 amp breaker in the main panel. My question is , I have a piece of #6 nmd, I know that your supposed to run thhn or rw90 in conduit, but I would like to use up this NMD, If I remove the jacket (outside sheathing) would this up to code?
Thanks in advance
Re: Sub Panel
Well technically it's not code because the wire is not marked. Code says the wire has to be marked. Wire that is inside sheathing is not marked because the sheath is. There is no problem doing it from a safety issue other than what is mentioned.
Tags for this Thread