Originally Posted by HornyPotter
people of little faith... red to breaker slug, black to the other slug of the breaker. no white.
how did i find out? cracked open the the load center, checked other 240v breakers, mimic what i saw and bingo... 240v!
saw the answer on another site? nah... did not bother going to any other site... such a good crowd here.
i wish you all a nice jolt of 240v!
back to you in the studio
What better way to learn electrical work. Simply copy what's already there.
View Tag Cloud