I'm not sure if i have this right......
Originally Posted by Josh
The power goes into you 2 gange box with your black white and bare wire, the provide power to your light and fan with the black white and bare going to each. are any of the wire touching the connections on your switch's? Turn off the circuit and wrap the back of the switch's with electrical tape. you then have your black white and bare head to your outlet from that box or is it a different Circuit. make sure your ground wire is not touching one of the other connections tap over all the screws on the back of your outlet. If none of that works and you are still having a short then you may have a staple that was to tight or a nail going through the wire. Hopefully you are able to get the wires. If you romex didn't run in the middle of the stud then you need to get a nailpalte to protect the wire where it is closer than 1 1/4 inchs to edge
Last edited by Polar Sparky 1224; 02-05-2006 at 09:54 PM.
"Diplomacy is saying nice dodging until you can find a rock." Will Rogers
"If a Monkey can do your job, are you in the right profession?