I'm not an electrician, so thanks for the vindication RMS. I think the point is that white is always supposed to be the neutral, correct, and experienced or not, I think wrapping the tape is there as a double check and a redundancy flag to make sure someone knows that the wire is definitely not neutral. Now that begs the point, does anyone know why the code requires white as hot wrappped, especially if its in a breaker?
Last edited by Roadrunner; 08-06-2006 at 07:38 PM.
Only a surfer knows the feeling. Billabong ca. 1985 or so